Automatic Fire Pit Igniter, Outdoor Fire Feature Control System - Electronic Flame Ignition
- 12 Volt System - Natural Gas or Propane
- INCLUDES: Pilot Shield, Transformer 12V, Pilot Tubing, Thermocouple, Hot Surface Ignitor, Pilot Injector (LP), Pilot Injector (Nat), Pilot Burner, Main Valve, Pilot Valve, Ignition Control
- COMPATIBLE WITH JANDY CONTROLLER
- Minimum Inlet Pressure: 0.25 psi Nominal Operating Inlet Pressure: 7" WC (NG) / 11" WC (LP)
- Best Price Point Automatic Fire Feature Controller On The Market! Burner Sold Separately.
Electrical Information Note: The 12 volt transformer supplied is to be located in a remote location away from the re feature in an approved weath- erproof electrical junction box and installed in accordance with local codes. Recommended Wire Size No less than 12 gauge wire for all installations Maximum Inlet Pressure: 1/2 psi Typical Pressure Requirements for Appliance: Minimum Inlet Pressure: 0.25 psi All connectors are water resilient. BASO BGA-171 series valve and pilot valve. Certi ed CSA 229521-1656058. Coils are encapsulated to protect against moisture. Pilot has robust ame pattern, wind resistant. Pilot injectors are stainless steel. Thermocouple is nickel plated for durability. CoorsTek HSI with protective cage. HSI connection is waterproof. The Power Wire connector is waterproof. Transformers are available. Safety or Active components are CSA Certi ed. 12 vac system to comply to NEC 2014 Article 680 require- ments. -20° to 175° temperature range. Durableconnectionsdesignedtoresistoutdoorconditions. 290,000 BTU’s at 1" pressure drop. TC Flame-sense system. Hot Surface Ignitor (HSI). LED diagnostics. Electronics are ANSI Z21.20-2014 certi ed. iFlame app is available as an option.
The ROCS Automatic Outdoor Control System is NOT an approved appliance. It is intended to be applied to appliances and burner systems supplied by various manufacturers. The ROCS in- structions are supplemental to the appliance manufacturers installation instructions. Installation of the ROCS system must be applied to an appliance approved by the appliance manufacturer and installed by a qualified professional. Failure to follow the manufacturers instructions, in addition to the ROCS installation instructions could result in property damage, injury or death. It is the responsibility of the installation professional and end user to confirm that the ROCS Control System is approved and safe to be used on the applied appliance or burner system. All BTU ratings and clearances to combustibles are solely defined by the appliance manufacturer. • Installation must conform with local codes or, in the absence of local codes, with the National Fuel Gas Code, ANSI Z223.1. • The appliance, when installed, must be electrically grounded in accordance with local codes or, in the absence of local codes, with the National Electric Code, ANSI/NFPA 70 (if applicable). FOR OUTDOOR USE ONLY! WARNING: If the information in these instructions in conjunction with the appliance man- ufacturers instructions are not followed exactly, a re may result causing property damage, personal injury or death. - Do not store or use gasoline or other ammable vapors and liquids in the vicinity of this or any other appliance. - WHAT TO DO IF YOU SMELL GAS • Do not try to light any appliance. • Do not touch any electrical switch; do not use any phone in your building. • Immediately call your gas supplier. Follow the gas supplier's instructions. • If you cannot reach your gas supplier, call the fire department. - Installation and service must be performed by a qualified installer, service agency or the gas supplier. WARNING: For use with Natural or Propane gas only. NO SOLID FUELS TO BE USED WITH THIS SYSTEM. WARNING: Placement of media (glass, lava, stone, etc.) MUST NOT cover the pilot assembly. WARNING: Check for gas leaks after installation is complete. WARNING: Inspect all components before installa- tion. If any parts are damaged, contact your supplier. Do not install damaged parts.